Testing of Plastics Piping Systems for a Lifetime of Confidence for Domestic Applications
Jul 18, 2022
The service life of plastics is generally determined by a combination of three factors; temperature, stress (pressure) and aggressive chemicals. Members of the BPF Pipes Group have piping products which undertake extensive testing at the extreme limits of these factors to ensure that they will give excellent performance in water systems.
In the UK, the service conditions for standard domestic applications can be found in BS 7291 “Thermoplastics pipe and fitting systems for hot and cold water for domestic purposes and heating installations in buildings.” These conditions are called ‘Class S’ and are as follows (Table 1 taken from BS 7291-1: 2010):
Nominal system flow temperature
Maximum system service temperature
System malfunction temperature
System maximum working pressure A)
|Indirect cold water systems||20||20||-||3½|
|Direct mains-fed cold water systems||20||20||-||12½|
|Subsurface heating systems||60||83||100||3½|
|Vented hot water supply systems||65||83||100||3½|
|Unvented hot water supply systems including Instantaneous heaters and/or incorporating storage||65||95||100||6|
|Vented central heating systems and indirect hot water primary circuits||82||95||100||3½|
|Sealed central heating systems and indirect hot water primary circuits||82||105||114||3|
Continuously operated re-circulating systems are excluded from these applications
A) Where a nominal working pressure does not comprise an integer value, the mantissa is
expressed in a fractional format. This is done to reduce the possibility of misinterpretation or
obscurity that could cause a system to be subjected to an excessive pressure.
B) 1 bar = 105N/mm2 = 105Pa
This standard (in common with the European Standards for plastics piping systems for hot and cold water installations) includes many tests which prove suitability for these applications. The tests are designed to replicate the conditions experienced by the pipe system in use at the limits of performance. These include:
- Confirmation of dimensions – the first and most important guarantee of the performance of a plastic pipe is sufficient wall thickness to resist pressure at temperature. The dimensions of outside diameter and wall thickness are specified in BS 7291 and are measured on a routine basis by pipe manufacturers.
- Long-term hydrostatic strength of pipes – it is essential to confirm the performance of the pipe over its whole design life. Holding samples of pipe at raised pressures at various temperatures for long periods of time generates data on times to failure. Pipes at higher pressures will burst sooner than those at lower pressures. Statistical analysis of the times to failure allows a robust prediction of the maximum pressure resistance of the pipe at over 50 years or beyond.
- Hydrostatic pressure resistance of assembled pipes and fittings – the strength of the joint between a pipe and fitting is critical to the lifetime success of a system. Pressurising samples of pipes and fittings together for 1,000 hours at pressures well above the Class S rating will verify this joint strength.
- Resistance to thermal cycling of assembled pipes and fittings – the temperature fluctuations and rapid thermal expansion and contraction encountered by a domestic hot water system or central heating system can induce stress in the pipework. This has the potential to damage or age the plastics being used. Subjecting pipe samples to thermal cycle testing involves creating a closed loop system which is repeatedly cycled with cold and hot water over three consecutive stages for approximately 7½ months. The test verifies the resistance of the system to this fluctuating stress.
- Resistance to cyclic pressure shock – pressure shocks can be experienced in water systems due to the rapid closing of valves or shutting down of pumps. Testing samples of pipe at 93°C and subjecting them to a 9-bar pressure shock every two seconds (30 cycles per minute), repeated 10,000 times, will rigorously confirm the resistance of pipes to these pressure shock conditions.
- Oxygen permeability (barrier pipe) – like metals, plastics can suffer oxidation in the presence of high levels of oxygen. Plastic pipes can be tailored to provide a barrier layer to oxygen permeability. This test confirms that the barrier is effective. The level of oxygen in a closed loop recirculating system is measured at very sensitive levels to ensure it is sufficiently low to prevent oxidation of the pipe or other system components (e.g. iron radiators).
Other short-term tests are designed to give manufacturers confidence that their piping system continues to meet the requirements on a day-to-day basis. These are basic pressure tests (at raised temperatures) over a short timeframe.
Factors in installation which can affect the lifetime of a plastics piping system
All members of the BPF Pipes Group provide extensive technical assistance on the correct installation of their systems. This information will help installers and end users maintain a correctly functioning system that will give many years of satisfactory service.
Further assistance can also be found in Building Regulations and installation standards BS EN 806 “Specification for installations inside buildings conveying water for human consumption” and BS 8558 “Guide to the design, installation, testing and maintenance of services supplying water for domestic use within buildings and their curtilages – complementary guidance to BS EN 806.”
In summary, the main advice points from manufacturers are:
- Use the piping system in applications for which it is designed
- Use connectors (and pipe inserts) compatible with the pipe
- Consult pipe sizing guides to guarantee sufficient flow
- Do not exceed the specified temperatures and pressures for the application (“Class S” BS 7291-1)
- Design the system to expand and contract freely during heating and cooling cycles
- Design the system to accommodate hot water expansion
- Do not put mechanical strain on a piping system
- Carefully follow manufacturer’s guidance when connecting to a boiler
- Protect from direct sunlight
- Do not bury pipe and fittings directly in concrete (except for underfloor heating pipe) INSTALLATION
- Protect pipework during installation from damage such as scratching, chemical attack by unsuitable substances (e.g. solder flux) or heat (e.g. blow torches)
- Do not use components that are obviously damaged
- Protect the pipework during service from freezing, direct mechanical abuse or attack by rodents
- Comply with electrical continuity requirements
- Do not bend pipework excessively, twist joints or apply side load
- Correctly support the pipe (consult manufacturer instructions on clipping)
Testing and Commissioning
- Ensure unvented hot water cylinders are functioning correctly
- Always pressure test systems before commissioning
- Always disinfect hot and cold water domestic systems before commissioning. When these sensible precautions are considered, plastics piping systems provide excellent performance in water systems over a long lifetime.
More News and Articles
May 30, 2023
Trenchless contractor puts maintenance hole relining system through its paces
Civil and trenchless specialists M Tucker & Sons showcases its expertise through a UV lining project.
May 26, 2023
City of Toronto launches tunnel boring machine for stormwater tunnel and largest basement flooding prevention project
Today, the City of Toronto marked a major milestone for the Fairbank Silverthorn Storm Trunk Sewer System project, launching a tunnel boring machine that will work to construct a new storm sewer that will collect, store and move stormwater from …
May 24, 2023
Global Water and Wastewater Utilities Take Aim at Climate Change
New Survey of 100 Utilities Tracks Net-Zero Progress: 75% of Respondents to Reduce Greenhouse Gas Emissions by 2040
May 22, 2023
Regional San’s monumental wastewater treatment plant expansion project delivered ON schedule and UNDER budget
The EchoWater Project, one of the largest public works projects in the Sacramento region’s history, takes wastewater treatment to a whole new level
May 19, 2023
Haliotis 2: Wastewater recovery and treatment complex
In April the future, next-generation wastewater recovery and treatment complex for the Métropole Nice Côte d’Azur “Haliotis 2” was presented. Christian Estrosi, Mayor of Nice, President of the Métropole Nice Côte d’Azur and Deputy President of the Région Provence-Alpes-Côte d’Azur …
May 17, 2023
Wrapping up the challenges in SA
In December 2022, Denso Australia completed the supply of a project involving the protection of 400 lineal metres of DN250 mild steel pipeline in Bolivar, South Australia.
May 15, 2023
New South Wales university receives network upgrade using SAERTEX-LINER® MULTI Type S+
Australian Pipeline Management (APM) has successfully relined three separate pipelines running under a university in Sydney with UV cured-in-place technology from SAERTEX multiCom® GmbH.
May 12, 2023
IMPREG continues to invest in Australian and NZ market
With increasing demand of IMPREG’s unique UV pipe solution, the German company continues to invest in the Australian and New Zealand market.
May 10, 2023
Yonge Street Project Combines Trenchless Rehab and New Install Practices
In the fall 2020, the Regional Municipality of York initiated a project to rehabilitate a 127 m long concrete box culvert under Yonge Street. The Region retained Jacobs Engineering to provide design and construction support services.
May 08, 2023
Climate adaption solutions for the water sector in the German-Danish border area
More than 60 participants met in Kolding, Denmark, from March 23 to 24 for the final conference of the INTERREG-Project NEPTUN. In the frame of this project, more than 40 partners elaborated 15 specific climate adaption solutions for the water …
May 05, 2023
Primus Line® flies the flag for trenchless solutions in sensitive locations
Primus Line has illustrated the benefits of trenchless technology for pipeline rehabilitation in culturally sensitive areas during two installations for one of the world’s leading mining companies.
May 03, 2023
Optimising chemical dosing in a challenging operating climate
Rising operating costs and tightening regulations are presenting major challenges for wastewater treatment plant operators, but better optimisation of chemical dosing can drive efficiencies, says Adeel Hassan, product manager at Watson-Marlow Fluid Technology Solutions.
The British Plastics Federation
6 Bath Place Rivington Street,
EC2A 3JE London
+44 (0) 20 7457 5000
+44 (0) 20 7457 5020