Testing of Plastics Piping Systems for a Lifetime of Confidence for Domestic Applications
Jul 18, 2022
The service life of plastics is generally determined by a combination of three factors; temperature, stress (pressure) and aggressive chemicals. Members of the BPF Pipes Group have piping products which undertake extensive testing at the extreme limits of these factors to ensure that they will give excellent performance in water systems.
In the UK, the service conditions for standard domestic applications can be found in BS 7291 “Thermoplastics pipe and fitting systems for hot and cold water for domestic purposes and heating installations in buildings.” These conditions are called ‘Class S’ and are as follows (Table 1 taken from BS 7291-1: 2010):
Nominal system flow temperature
Maximum system service temperature
System malfunction temperature
System maximum working pressure A)
|Indirect cold water systems||20||20||-||3½|
|Direct mains-fed cold water systems||20||20||-||12½|
|Subsurface heating systems||60||83||100||3½|
|Vented hot water supply systems||65||83||100||3½|
|Unvented hot water supply systems including Instantaneous heaters and/or incorporating storage||65||95||100||6|
|Vented central heating systems and indirect hot water primary circuits||82||95||100||3½|
|Sealed central heating systems and indirect hot water primary circuits||82||105||114||3|
Continuously operated re-circulating systems are excluded from these applications
A) Where a nominal working pressure does not comprise an integer value, the mantissa is
expressed in a fractional format. This is done to reduce the possibility of misinterpretation or
obscurity that could cause a system to be subjected to an excessive pressure.
B) 1 bar = 105N/mm2 = 105Pa
This standard (in common with the European Standards for plastics piping systems for hot and cold water installations) includes many tests which prove suitability for these applications. The tests are designed to replicate the conditions experienced by the pipe system in use at the limits of performance. These include:
- Confirmation of dimensions – the first and most important guarantee of the performance of a plastic pipe is sufficient wall thickness to resist pressure at temperature. The dimensions of outside diameter and wall thickness are specified in BS 7291 and are measured on a routine basis by pipe manufacturers.
- Long-term hydrostatic strength of pipes – it is essential to confirm the performance of the pipe over its whole design life. Holding samples of pipe at raised pressures at various temperatures for long periods of time generates data on times to failure. Pipes at higher pressures will burst sooner than those at lower pressures. Statistical analysis of the times to failure allows a robust prediction of the maximum pressure resistance of the pipe at over 50 years or beyond.
- Hydrostatic pressure resistance of assembled pipes and fittings – the strength of the joint between a pipe and fitting is critical to the lifetime success of a system. Pressurising samples of pipes and fittings together for 1,000 hours at pressures well above the Class S rating will verify this joint strength.
- Resistance to thermal cycling of assembled pipes and fittings – the temperature fluctuations and rapid thermal expansion and contraction encountered by a domestic hot water system or central heating system can induce stress in the pipework. This has the potential to damage or age the plastics being used. Subjecting pipe samples to thermal cycle testing involves creating a closed loop system which is repeatedly cycled with cold and hot water over three consecutive stages for approximately 7½ months. The test verifies the resistance of the system to this fluctuating stress.
- Resistance to cyclic pressure shock – pressure shocks can be experienced in water systems due to the rapid closing of valves or shutting down of pumps. Testing samples of pipe at 93°C and subjecting them to a 9-bar pressure shock every two seconds (30 cycles per minute), repeated 10,000 times, will rigorously confirm the resistance of pipes to these pressure shock conditions.
- Oxygen permeability (barrier pipe) – like metals, plastics can suffer oxidation in the presence of high levels of oxygen. Plastic pipes can be tailored to provide a barrier layer to oxygen permeability. This test confirms that the barrier is effective. The level of oxygen in a closed loop recirculating system is measured at very sensitive levels to ensure it is sufficiently low to prevent oxidation of the pipe or other system components (e.g. iron radiators).
Other short-term tests are designed to give manufacturers confidence that their piping system continues to meet the requirements on a day-to-day basis. These are basic pressure tests (at raised temperatures) over a short timeframe.
Factors in installation which can affect the lifetime of a plastics piping system
All members of the BPF Pipes Group provide extensive technical assistance on the correct installation of their systems. This information will help installers and end users maintain a correctly functioning system that will give many years of satisfactory service.
Further assistance can also be found in Building Regulations and installation standards BS EN 806 “Specification for installations inside buildings conveying water for human consumption” and BS 8558 “Guide to the design, installation, testing and maintenance of services supplying water for domestic use within buildings and their curtilages – complementary guidance to BS EN 806.”
In summary, the main advice points from manufacturers are:
- Use the piping system in applications for which it is designed
- Use connectors (and pipe inserts) compatible with the pipe
- Consult pipe sizing guides to guarantee sufficient flow
- Do not exceed the specified temperatures and pressures for the application (“Class S” BS 7291-1)
- Design the system to expand and contract freely during heating and cooling cycles
- Design the system to accommodate hot water expansion
- Do not put mechanical strain on a piping system
- Carefully follow manufacturer’s guidance when connecting to a boiler
- Protect from direct sunlight
- Do not bury pipe and fittings directly in concrete (except for underfloor heating pipe) INSTALLATION
- Protect pipework during installation from damage such as scratching, chemical attack by unsuitable substances (e.g. solder flux) or heat (e.g. blow torches)
- Do not use components that are obviously damaged
- Protect the pipework during service from freezing, direct mechanical abuse or attack by rodents
- Comply with electrical continuity requirements
- Do not bend pipework excessively, twist joints or apply side load
- Correctly support the pipe (consult manufacturer instructions on clipping)
Testing and Commissioning
- Ensure unvented hot water cylinders are functioning correctly
- Always pressure test systems before commissioning
- Always disinfect hot and cold water domestic systems before commissioning. When these sensible precautions are considered, plastics piping systems provide excellent performance in water systems over a long lifetime.
More News and Articles
Aug 11, 2022
WPL has been granted a patent for its cutting-edge WPL Hybrid-SAFTM process technology. The patented technology employs a submerged moving-bed, fixed-film reactor which can treat wastewater with greater energy efficiency compared to traditional submerged aerated filters (SAFs), in a tighter …
Aug 11, 2022
Awarded more than £700,000 from the Water Breakthrough Challenge Catalyst Stream, Treatment-to-Tap seeks an industry watershed by supplementing a tech rollout with collaborative data analysis and behavioural science to build trust in tap water.
Aug 10, 2022
Water sector specialist MWH Treatment has been awarded a place on Severn Trent’s AMP7 (regulatory asset management period 2020-25) framework for both design-and-build and build-only water and wastewater treatment projects. The agreement extends an existing 20-year relationship and MWH Treatment …
Aug 09, 2022
For the rehabilitation of a drinking water pipeline in the district of Aalen, 200 km north-east of Munich, Germany, the DENSO Group Germany protects weld seams from corrosion very quickly and efficiently using a new laying method that floats in …
Aug 08, 2022
With construction work being carried out in depths up to 30 metres in the centre of the city famous for the Golden Gate Bridge, an enormous building structure is being realised. When completed, the Chinatown Subway Station will form the …
Aug 05, 2022
Development for the American Biotech company
Aug 04, 2022
The Construction Site Determines the Installation Technology: Light, Steam, Hot Water or Ambient Temperature
Which curing method should ideally be used in the context of rehabilitation projects in building and site drainage? The market for the rehabilitation of building and property drainage is currently developing dynamically. The complexity of construction sites in particular places …
Aug 03, 2022
100 Years Lifetime of Polyethylene Pressure Pipe Systems Buried in the Ground for Water and Natural Gas Supply
TEPPFA and PE100+ Association have identified the need for explaining the difference between the design point at 20 degree/50 years and the expected life-time of PE80 and PE100 pressure pipe systems. Research, extrapolation studies and reports on dig-up pipes in …
Aug 02, 2022
United Utilities is rolling out the biggest “listening” project of its kind in the world in a bid to tackle water leakage. The North West water company is installing around 100,000 ‘acoustic’ loggers over the next two years on its …
Aug 01, 2022
A dense pipeline network spanning over three million kilometers is the global backbone of industry and commerce. To keep supply stable, innovative pipeline companies are constantly expanding the network and making it denser even in sparsely populated places. In the …
Jul 29, 2022
Surface heating and cooling using plastic pipes is being highlighted at the moment as it is helping facilitate a greater uptake of renewable heat sources and is proving highly energy-efficient in our increasingly energy-aware climate.
Jul 27, 2022
Wastewater treatment specialist WPL has won a contract to provide onsite wastewater treatment at a holiday park in Cornwall. The underground installation at Juliots Well in North Cornwall will replace the existing septic tank and includes a WPL HiPAF (high …