Pumps for the 21st Century
May 23, 2022
The Pump Centre Conference offers a range of sessions headed by experts in their field. Here’s a precis of those talks made available so far, beginning with Smith & Loveless’ Andrew Hornabrook who considers the demands of optimising force main pressure from multiple pump stations.
Given the resulting variable pressure that occurs in the force main is dependent on how many pump stations are operating at one time, designers face incorporating solutions that are costly from a capital and operational standpoint.
The problem is that the force main pressure can be low when only one pump station is operating or much higher when multiple pump stations operate at the same time. The pump station must be designed to handle the worst condition – when all the pump stations are operating at the same time, resulting in the highest force main pressure to overcome.
However, if this is the only condition they are designed for, the pump will vastly over pump when fewer pump stations are operating. This can result in pumps running out on the pump curve, exceeding the maximum motor amp draw. Yet, if the additional pressure is not incorporated in the design, the pumps will go to shutoff at the high-pressure condition and wet well overflows can occur.
Without accounting for the variable conditions, reduced service life and a multitude of problems can result. When you operate a pump outside of its normal operating range you run the risk of low and high flow cavitation. These phenomena result in impeller and volute erosion, reduced bearing and seal life, excessive pump noise and vibration.
- Costly communication systems, tying all the pump stations together, which limit the number of pump stations on line at the same time
- Oversizing the pump and/or pump motor
- Orifice plates or partially closed discharge valves to create artificial head and prevent run-out – resulting in increased energy usage and increased chances for choked piping
- Installation of a flow meter with feedback loop to a VFD to maintain a constant flow rate regardless of head. The flowmeter complicates the operation of the station and requires additional infrastructure.
Smith & Loveless sought a better solution to provide longer pump life, reduced operation and maintenance time and cost, reduced capital expenditure, all designed to fit within one of its offsite built pump stations. By utilising the S&L QUICKSMART™ PLC pump station controller with colour touchscreen HMI, a variable frequency drive and a force main sensor, the PLC can receive a signal from the sensor indicating changes in the force main due to additional pump stations coming on or going off.
From this information, an algorithm embedded in the PLC calculates the correct frequency for the VFD to adjust the pump speed to maintain a constant flow rate no matter how many stations are on line.
Monitoring the force main and pump speed via a patented algorithm, it becomes easy to add a standalone pump station to a common force main with multiple pump stations already in service.
It eliminates the headaches and costs of adding elaborate communication systems, oversized pumps, installing costly flow meters or greatly increasing the possibility of clogging.
More News and Articles
Dec 04, 2023
In an effort to combat water loss, a global collaboration involving organizations from the UK, US, and Mexico is launching a long-term project in Querétaro, Mexico. Utilizing actionable AI, the initiative aims to manage and conserve water resources across 350km …
Dec 01, 2023
A microtunnel boring machine (TBM) has arrived on Elizabeth Street to help deliver one of the biggest upgrades to Melbourne CBD’s sewer network in more than a century.
Nov 29, 2023
Researchers at MIT (Massachusetts Institute of Technology) have made a groundbreaking discovery that could change our understanding of evaporation, a ubiquitous process in our environment. They found that under certain conditions, light can directly cause evaporation without the need for …
Nov 27, 2023
NEW UNITRACC Construction Site Documentation: "Rehabilitation of a DN 400 Concrete Gravity Sewer with a SAERTEX-LINER® MULTI over a Length of 69 m" (CIPP)
New construction site documentation in the renovation section of the e-learning platform: Rehabilitation of a DN 400 concrete gravity sewer with CIPP lining using SAERTEX-LINER® MULTI, type S+ Standard. The objective of this rehabilitation measure was to enhance the structural …
Nov 27, 2023
Digitising water management
Nov 24, 2023
Budleigh Salterton is a popular and picturesque seaside town situated within the East Devon Area of Outstanding Natural Beauty. Located at the start of the stunning Jurassic Coast; a UNESCO World Heritage Site recognised for its outstanding rocks, fossils and …
Nov 22, 2023
Having been in business for 86 years, Interflow has proven it knows a thing or two about longevity. Right now, that requires an all-encompassing sustainability strategy, as Richard McCarthy, Interflow’s executive general manager southern region, explained.
Nov 20, 2023
An interview with Managing Director Robert Ristow
Nov 17, 2023
Tractebel and Aurecon forge strategic partnership to revolutionize dam projects in Queensland, Australia
Tractebel and Aurecon form a strategic alliance to revolutionize dam projects in Queensland, Australia, combining their global expertise and local knowledge to meet the rising demand for dam upgrades.
Nov 15, 2023
SA Water will use horizontal directional drilling (HDD) to assist in installing a section of pipe underneath the Melbourne to Adelaide rail corridor.
Nov 13, 2023
Saudi Arabia’s visionary city, Neom, is leading the way in sustainable water solutions with the construction of a desalination plant powered entirely by renewable energy.
Nov 10, 2023
Adept Civil Group has successfully delivered on a sewer reticulation extension project at the Charlemont Rise estate.