Pumps for the 21st Century
May 23, 2022
The Pump Centre Conference offers a range of sessions headed by experts in their field. Here’s a precis of those talks made available so far, beginning with Smith & Loveless’ Andrew Hornabrook who considers the demands of optimising force main pressure from multiple pump stations.
Given the resulting variable pressure that occurs in the force main is dependent on how many pump stations are operating at one time, designers face incorporating solutions that are costly from a capital and operational standpoint.
The problem is that the force main pressure can be low when only one pump station is operating or much higher when multiple pump stations operate at the same time. The pump station must be designed to handle the worst condition – when all the pump stations are operating at the same time, resulting in the highest force main pressure to overcome.
However, if this is the only condition they are designed for, the pump will vastly over pump when fewer pump stations are operating. This can result in pumps running out on the pump curve, exceeding the maximum motor amp draw. Yet, if the additional pressure is not incorporated in the design, the pumps will go to shutoff at the high-pressure condition and wet well overflows can occur.
Without accounting for the variable conditions, reduced service life and a multitude of problems can result. When you operate a pump outside of its normal operating range you run the risk of low and high flow cavitation. These phenomena result in impeller and volute erosion, reduced bearing and seal life, excessive pump noise and vibration.
- Costly communication systems, tying all the pump stations together, which limit the number of pump stations on line at the same time
- Oversizing the pump and/or pump motor
- Orifice plates or partially closed discharge valves to create artificial head and prevent run-out – resulting in increased energy usage and increased chances for choked piping
- Installation of a flow meter with feedback loop to a VFD to maintain a constant flow rate regardless of head. The flowmeter complicates the operation of the station and requires additional infrastructure.
Smith & Loveless sought a better solution to provide longer pump life, reduced operation and maintenance time and cost, reduced capital expenditure, all designed to fit within one of its offsite built pump stations. By utilising the S&L QUICKSMART™ PLC pump station controller with colour touchscreen HMI, a variable frequency drive and a force main sensor, the PLC can receive a signal from the sensor indicating changes in the force main due to additional pump stations coming on or going off.
From this information, an algorithm embedded in the PLC calculates the correct frequency for the VFD to adjust the pump speed to maintain a constant flow rate no matter how many stations are on line.
Monitoring the force main and pump speed via a patented algorithm, it becomes easy to add a standalone pump station to a common force main with multiple pump stations already in service.
It eliminates the headaches and costs of adding elaborate communication systems, oversized pumps, installing costly flow meters or greatly increasing the possibility of clogging.
More News and Articles
Mar 01, 2024
Researchers in the UK and Germany have developed a new approach for detecting pollution from ‘forever chemicals’ in water through luminescence.
Feb 28, 2024
This study presents BioElectrochemical Treatment Technology (BETT) as a new wastewater management solution toward the Net-Zero future. The results reported herein were collected from a BETT pilot system installed at a large brewery in Los Angeles, CA, United States processing …
Feb 26, 2024
Following the successful pilot of its digital asset management technology with Anglian Water, Norwegian digital analytics company InfoTiles is embarking on an expanded proof of concept programme.
Feb 23, 2024
NLN Farms, located near the coastal town of Chocowinity, North Carolina, needed to transfer water from four aquaculture ponds to a nearby reservoir. The farm selected Xylem's Godwin CD100 dewatering pump for the job, with Field Smart Technology, which enables …
Feb 21, 2024
Following the devastating flooding from Cyclone Gabrielle in 2023, Watercare is acknowledging the ongoing recovery efforts one year on.
Feb 19, 2024
Our panel of international experts examines how utilities can embrace a global outlook when it comes to security.
Feb 16, 2024
The Silver Creek Water Corporation in southern Indiana manages millions of gallons of water, over hilly terrain, for 20,000 people. Over several decades, the utility has deployed technology from Xylem’s Sensus brand to remotely manage meters, prevent water loss and …
Feb 14, 2024
As the underground grows more crowded, the industry is under pressure to deliver highly accurate installations through a web of existing infrastructure.
Feb 12, 2024
In a new study, scientists at Heriot-Watt University have discovered a sustainable method to produce green hydrogen, a type of renewable fuel, using wastewater from the distilling industry. This new approach not only addresses the global challenge of water scarcity …
Feb 09, 2024
The UK water sector should give more focus to the themes of delivering resilient infrastructure systems and protecting and enhancing natural systems, according to a survey about the UK 2050 Water Innovation Strategy.
Feb 07, 2024
Drinking water scarcity is a global issue, including in Sweden, where it’s also used for crop irrigation and various industrial operations. This practice is neither sustainable nor efficient. Hence, MDU has launched an innovative research project aimed at developing efficient …
Feb 05, 2024
Industrial companies and commercial building owners wanting to reduce waste to improve cost efficiency and save water, must become smarter in their operations, writes Paul Hartley, chief commercial officer, Ovarro