What`s in the Numbers?
Jul 30, 2014
A Review and Analysis of More than 400 Miles of Force Main Inspection and Condition Assessment Data.
Comprehensive condition assessment of wastewater force mains provides significant challenges to owners/operators of collection systems as the ability to shut down or expose the pipeline for a thorough inspection is often impractical due to operational and/or financial considerations.Traditional gravity sewer inspection techniques (i.e. visual based technologies) do not always transfer easily to their wastewater pressure pipe counterparts and visual assessments do not provide the structural condition of force main – something that is critical in determining the true pipe condition. Therefore, a different set of inspection tools and assessment techniques is required for force mains.
The most effective strategy to safely manage a force main inventory is to implement a risk based approach for any data collection, inspection, condition assessment, and management techniques. Using asset risk to guide the management strategies, an owner/operator can ensure they are implementing the right approach, at the right time, with the lowest financial impact. While, recent advances in force main inspection technologies, assessment techniques, and repair/rehabilitation methods now allow for substantial extension of existing asset service life, a risk based approach to their implementation will ensure resources are focused on the correct pipelines. The goal should always be to focus the proper resources in managing the asset while safely getting the most service life out of the force main.
Wastewater utilities in the United States focus significant resources towards the evaluation of their collection system performance due to regulatory pressure, public health concerns, and a focus on proper asset management practices. Evaluations have primarily focused on the gravity collection system through capacity and condition assessments resulting in rehabilitation and replacement programs often influenced by regulatory drivers. The assessment, rehabilitation, and replacement components provide the utility with the ability to better manage their wastewater water collection system and thereby reducing illegal discharges to the environment and protecting public safety. Capacity and condition assessments have become increasingly more effective through advancements in the assessment technologies.
Specifically, flow metering, hydraulic modeling, robotic inspection, and trenchless rehabilitation/replacement technology advancements over the past several years have allowed wastewater utilities to efficiently understand the condition of the buried infrastructure as well as effectively extend the useful life and manage these assets. The assessment technology advancements provide higher quality data allowing for a thorough understanding of a collection system’s existing capacity, inflow and infiltration sources, as well as operational and structural defects that can be addressed through rehabilitation and/or replacement action. Gravity mains are typically assessed in a programmatic approach known as a sewer system evaluation survey (SSES).
A SSES typically follows the following methodology.
- Implementation of a comprehensive flow metering program to identify areas with high wet weather peak flows
- Targeted smoke testing in areas identified by the flow metering program locating potential inflow sources
- Dye testing to confirm smoke testing results (i.e. inflow sources)
- Areas identified with excessive groundwater infiltration through the flow metering program then undergo night flow isolation tests
- Finally, a closed circuit television (CCTV) inspection of pipes with high night flow isolation rates is conducted in order to identify operational and structural defects leading to infiltration as well as pipeline blockages.
While this process and individual techniques are effective in assessing gravity wastewater systems, they do not always transfer easily to the wastewater pressure pipe (force main) system. If a force main can be temporarily taken out of service with internal access provided via an entry port, an inspection can be conducted in order to determine the condition of the pipeline using traditional techniques (including CCTV, SONAR, and/or laser profiling) or technologies to assess the internal corrosion of the pipe. However, since wastewater force mains are generally designed with little to no redundancy or internal pipeline access (taps, entry ports, etc.), these invasive assessment technologies are often not applicable. Plus, external corrosion is a frequent cause of failure for force mains, which will not be assessed through these tradition gravity sewer inspection techniques. Therefore, wastewater force main condition assessment programs need to take a different approach than the SSES protocol outlined above.
- Conduct an analysis of the collection system force mains to identify the high risk pipelines using a likelihood of failure rating based on the structural and operational condition of the pipeline as well as the consequence of failure rating, which accounts for direct cost, health/environmental, and socio-economic factors. In simple terms, asset management principles define risk as a product of consequence of failure and likelihood of failure (COF x LOF). Unlike what has been the industry standard in years past, this risk assessment should not be used as a replacement strategy but a prioritization of where to collect more data on the pipelines. The reason for this is based on data collected not only by the authors of this paper, but also the Environmental Protection Agency that indicates that between 70% and 90% of the pipe being replaced in the United States has physical life left;
- Based on the risk assessment, develop a risk based inspection and condition assessment strategy that uses technologies, engineering, and analysis that optimizes human and financial resources all while reducing the risk of each pipeline asset to an acceptable level. Figure 2.2 provides a simplified approach to implementing a force main management strategy using a risk base approach. As the risk of each asset increases, the inspection technology resolution as well as the analysis technique complexity increases (these area additive as risk increases). While this also increases the cost of the assessment, the reliability of the information also increases thereby reducing the risk of managing the asset;
- Data from the corrosion source identification and pipe wall integrity techniques can then be used to provide inputs to both structural and statistical analysis. These analyses provide the wastewater utility with the remaining useful life of the force main and will assist in the development of rehabilitation or replacement strategies;
- Once a force mains condition and remaining useful life is known, a comprehensive pipeline management strategy should be developed, which may include future inspection strategies/schedules, rehabilitation or replacement strategies (CIP planning), detailed pipeline data for asset management systems, etc.
Using a risk based approach to pipeline management for more than 500 miles of force mains, data indicates that these critical pipelines typically do not deteriorate or fail systematically along their full length. Instead, deterioration usually consists of localized problems due to environmental or operational factors. Force main inspection and condition assessment data indicates that less than 10% of the pipelines surveyed have indicators of distress while even less (approximately 1%) require repair or replacement to extend their service life.
For example, a recently completed a force main condition assessment of nearly 3.5 miles of ductile iron pipe indicated that less than 5% of the force main alignment was found to have gas pockets, which can create conditions for internal corrosion and is the primary cause of ferrous force main failures, but pipe wall assessment measurements reveled the pipe to be of adequate thickness. Installation of air release valves was recommended to evacuate the trapped gas, but no other repairs are required saving the client significant capital and operational resources.
2.1. Force Main Inventory and Failure Modes
It is important to note that defects and deterioration of force mains can be wide ranging and may vary from one pipe material to another. Therefore it is often prudent to implement multiple techniques and technologies using on the previously described risk based approach. Too often, inspection techniques and assessment strategies are implemented without consideration of the particular force main characteristics, its threats, and ultimate informational needs for the pipeline. This depletes valuable financial and operational resources without providing the necessary information for managing the pipeline.
2.2. Force Main Assessment Techniques
Force main inspection technology selection is a key part of any management program and requires a sound technical understanding of the various tools available in the industry. Prior to developing any inspection and assessment planning protocols force main inventories, it is critical for key stakeholders to understand the available technologies used for destructive and nondestructive testing of pressure pipelines. Some of the variables that must be evaluated when selecting technologies for assessing a pipeline may include:
- Force Main Risk
- Pipe Material
- Pipe Diameter and Length
- Operational Constraints
- Pipeline Inspectability
- Cost Efficiency of Technologies
- Technology Limitations
- Ability to Provide Actionable Information
It is important to note that defects and deterioration of force mains can be wide ranging and can vary from one pipe material to another. To identify different defects in force mains, it is often prudent to use multiple techniques and technologies. Too often, inspection techniques and assessment strategies are implemented without consideration of the particular force main characteristics, its threats, and ultimate informational needs for the pipeline. By using this "broad brush approach" to force main assessment, valuable financial and operational resources are often depleted without providing the necessary information for managing the pipeline. Therefore, this paper will not outline various inspection techniques or technologies available in the industry but rather focuses on the analysis of data and overall management approach.
3. Remaining Useful Life Analysis
3.1 Ferrous Force Mains
In order to predict the likely remaining useful life of ferrous force mains, statistical analyses can be developed that utilizes the inspection data collected as well as the engineering analysis performed that determines the existing condition. In order to perform this evaluation, a minimum amount of data must be collected in order to provide useful, actionable information. This minimum data may include:
- A required quantity of pipe wall integrity measurements in order to achieve a desired confidence level (e.g. 95%);
- Adequate data collection methodology to assume the results are representative of the force main;
- Ability to either predict a deterioration rate based on previously collected data or scientifically defensible assumptions;
- Structural analysis based on operating conditions, design standards/details, current condition, etc.
Of note, corrosion rates for the force main based on the external corrosion survey results (indirect) versus the pipe wall thickness measurement results (direct) in order to determine the correlation between data. Figure 3.2 displays two normal probability density functions for each data set indicating little correlation.
3.2. Concrete Force Mains (Prestressed Concrete Cylinder Pipe – PCCP)
A predictive model can be used to estimate when re-inspection intervals, monitoring strategies, and capital planning. This model incorporates historical information, inspection data, the structural analysis, and design/installation information of the subject pipeline while leveraging existing knowledge of force main condition assessment and comprehensive data on real-time monitoring of PCCP at various locations throughout the US.
The predictive model first considers each distress indicator collected during the leak and gas pocket detection and electromagnetic inspections. The distress indicators considered in this analysis may include:
- Number of broken wire wraps
- Number of wire wrap break zone
- Location of wire wrap break
- Presence of gas pocket
- Presence of leaks
The magnitude or presence of each distress indicator is related to the condition of each pipe section by use of a condition-state matrix. This condition-state matrix has been described previously by the author and can be found in the proceedings of the NASTT No-Dig Show (2011). The condition-state matrix that relates the distress indicators listed above to possible condition-states based on PCCP designs, performance curves (structural analysis), history of the force mains, and experiential knowledge. Once the condition rating for each pipe is derived, a deterioration model can be used to simulate pipe degradation. For an individual pipe, this leads to overall degradation via transition from one condition-state to the next until reaching a failed state.
Ideally, it is best to re-inspect force mains before a high likelihood of failure. Using these criteria, Figure 3.4 indicates that re-inspection of the sample force main should occur in 4 to 5 years.
3.3 Limitations to the Models (Ferrous and Concrete)
It is important to discuss some of the assumptions and limitations of this analysis. First, this analysis does not guarantee that there will be no force main failures within the time until reinspection is recommended. Rather, this analysis states that if re-inspection is not completed within the recommended time, there is a higher possibility of force main failure. This analysis considers all degradation rates observed in force mains; however, experiential knowledge dictates that there is considerable variability in the degradation of individual pipe sections, even those within the same pipeline (i.e. it cannot be guaranteed that a pipe section will not degrade faster than previously observed in a pipeline).
In addition, this analysis must be re-evaluated if there are operational changes to the pipeline that vary significantly from historic operations. For example, if the flow rate is decreased to a point where significant gas pockets can exist within the force main and possibly lead to H2S corrosion, the recommended time until re-inspection would be too liberal. Lastly, this analysis does not assume the installation of any monitoring technologies. If the client did decide to install real-time monitoring technology, the recommended time until re-inspection would be overly conservative.
The management of force mains has significantly advanced over the past decade first through development of inspection techniques/technologies then the analytical and engineering support behind these tools. While many tools now exist to provide a snapshot of a force main condition, not all technologies are created equal and provide various levels of data resolution and reliability. Therefore, approaching technology selection and subsequent analysis should be based on the risk of the force main. In order to determine this risk, the likelihood and consequence of failure must be evaluated to adequately inform these decisions.
By understanding the risk of the force main along with the benefits and limitations of assessment techniques/technologies, a sound defensible management strategy can be implement to maintain and extend the life of the asset. Too often, not enough or the right information is collected to make informed decisions on managing a force main often causing utilities to replace assets with significant physical life remaining. This is frequently the result of improper assessment technique/technology selection and data interpretation. Also, being overly budget conscience when it comes to obtaining a sound baseline for the force main condition often results in larger capital expenditures on rehabilitation/replacement or increased risk of failure. Therefore, by approaching force main management with a risk based strategy, these assets can provide continued service at an optimized life-cycle cost.
(Authors: Travis B. Wagner, Pure Technologies Ltd., Columbia, MD, USA / Jennifer Steffens, Pure Technologies Ltd., Atlanta, GA, USA)
More News and Articles
May 30, 2023
Trenchless contractor puts maintenance hole relining system through its paces
Civil and trenchless specialists M Tucker & Sons showcases its expertise through a UV lining project.
May 26, 2023
City of Toronto launches tunnel boring machine for stormwater tunnel and largest basement flooding prevention project
Today, the City of Toronto marked a major milestone for the Fairbank Silverthorn Storm Trunk Sewer System project, launching a tunnel boring machine that will work to construct a new storm sewer that will collect, store and move stormwater from …
May 24, 2023
Global Water and Wastewater Utilities Take Aim at Climate Change
New Survey of 100 Utilities Tracks Net-Zero Progress: 75% of Respondents to Reduce Greenhouse Gas Emissions by 2040
May 22, 2023
Regional San’s monumental wastewater treatment plant expansion project delivered ON schedule and UNDER budget
The EchoWater Project, one of the largest public works projects in the Sacramento region’s history, takes wastewater treatment to a whole new level
May 19, 2023
Haliotis 2: Wastewater recovery and treatment complex
In April the future, next-generation wastewater recovery and treatment complex for the Métropole Nice Côte d’Azur “Haliotis 2” was presented. Christian Estrosi, Mayor of Nice, President of the Métropole Nice Côte d’Azur and Deputy President of the Région Provence-Alpes-Côte d’Azur …
May 17, 2023
Wrapping up the challenges in SA
In December 2022, Denso Australia completed the supply of a project involving the protection of 400 lineal metres of DN250 mild steel pipeline in Bolivar, South Australia.
May 15, 2023
New South Wales university receives network upgrade using SAERTEX-LINER® MULTI Type S+
Australian Pipeline Management (APM) has successfully relined three separate pipelines running under a university in Sydney with UV cured-in-place technology from SAERTEX multiCom® GmbH.
May 12, 2023
IMPREG continues to invest in Australian and NZ market
With increasing demand of IMPREG’s unique UV pipe solution, the German company continues to invest in the Australian and New Zealand market.
May 10, 2023
Yonge Street Project Combines Trenchless Rehab and New Install Practices
In the fall 2020, the Regional Municipality of York initiated a project to rehabilitate a 127 m long concrete box culvert under Yonge Street. The Region retained Jacobs Engineering to provide design and construction support services.
May 08, 2023
Climate adaption solutions for the water sector in the German-Danish border area
More than 60 participants met in Kolding, Denmark, from March 23 to 24 for the final conference of the INTERREG-Project NEPTUN. In the frame of this project, more than 40 partners elaborated 15 specific climate adaption solutions for the water …
May 05, 2023
Primus Line® flies the flag for trenchless solutions in sensitive locations
Primus Line has illustrated the benefits of trenchless technology for pipeline rehabilitation in culturally sensitive areas during two installations for one of the world’s leading mining companies.
May 03, 2023
Optimising chemical dosing in a challenging operating climate
Rising operating costs and tightening regulations are presenting major challenges for wastewater treatment plant operators, but better optimisation of chemical dosing can drive efficiencies, says Adeel Hassan, product manager at Watson-Marlow Fluid Technology Solutions.
Pure Technologies Ltd.
8920 State Route 108, Suite D
+1 (443) 766-7873
+1 (443) 766-7877