Manor farm harvests heat
Sep 21, 2010
Manor Farm is situated on some of the most fertile planes in rural Bedfordshire. It is located on the edge of the beautiful village of Eyeworth and was constructed in 1865. Traditional arable and livestock farming methods were the order of the day on this once very busy farm.
This delightful Georgian-style farmhouse and buildings were recently purchased by Charles and Karen Sterling as a family home, together they drew up a sympathetic detailed restoration and modernisation plan of the building. This incorporated under floor heating and with Cº2 emissions, operational efficiency and lowest running costs in mind, they opted for a Ground Source Heat Pump to provide heating and hot water. So would begin the harvesting of sustainable Geothermal Energy whenever required, significantly reducing their heating costs.
Following careful consideration of the Heat Well’s design and in conjunction with ground water drillers and geothermal heat well specialists, Warren Ecological, the Geothermal Radial Drilling (GRD) method was chosen. Bob Evans, Warren’s Managing Director, said GRD provides a completely integrated drilling technique and solutions to a number of issues with this type of retrofit project. Warren were working with Roland Amey Renewables, the warm side designers, to install the NIBE Ground Source Heat Pump.
GRD is the innovative geothermal slant drilling system from manufacturers TT-UK (GRD) Ltd, part of the TT Group. GRD is designed to search out the most rewarding geology maximising heat well efficiency. Use of all land within the plot boundary can be considered without affecting its future use. Importantly it is also quite simple to increase the heat well capacity at a later date if for example the property is increased in size.
The project called for a total heat requirement of 30 kW, ten x fifty metre long bore holes would be drilled radially spaced to avoid borehole interference at varying angles between 65º and 35º down, over a radius of just 180 º
The Job site set up was rapid due to careful planning by Warren; the GRD 4R rig, just 1.5m wide, weighing 2700kg, was tracked and connected to its pre-positioned drill chamber for the whole of the drilling process. This completely avoids any potential damage to the immediate environment and garden. The integral drill rod and casings lifting hoist was then erected and the HSE safety platform connected, this reduces the rigs spindle rotation to a safe max 10 rpm when connecting and disconnecting all drill rods and casings to one another.
A Geological Survey indicated a mixture of clay, silt and sand, so water flushing using a conventional three winged drag bit, constant displacement pump and three settlement tanks were used. The Geology Report turned out to be reasonably accurate; geology was recorded rod by rod from the first bore to prove the drill plans and heat extraction values. The Geology remained the same throughout. The last 31 metres of every bore hole was green sand. This was cut and flushed out using a drag bit, constant displacement pump and a three settlement tank water recycling method. All borehole cuttings were returned into the settlement tanks avoiding ground or airborne overspill, leaving a clean and tidy site. TT-UK (GRD) have also developed a single container (skip) water loss method, where the pump recycles the flushing fluid which collects the cuttings and deposits them in a skip displacing the water. When full the skip is removed and a replacement provided if required.
With the first borehole at 50m long x 65º down, all drill rods were extracted and a Fusion co-axial (pipe inside pipe) collector was installed with grouting tube and pressure tested using a digital datalogger with an analogue pressure gauge back-up. This data is recorded for inclusion in the GRD Heat Well Owner’s Manual which also includes the drill plan, geology report, bore hole geology (real time) drill log and property heat requirement calculations.
All borehole collectors were made from one piece PE100/SDR 11 material and connect to the manifold fitted to the inside of the drill chamber.
Grouting: Following satisfactory pressure test results, grouting was carried out using thermal conductive ready mixed grout powder. A small integral hopper is filled with dry grout and mixed with water to the correct viscosity to suit both ground water flow rates and bore hole conditions. This took place from the bottom up by draining the grout pipe as the annulus filled. All drill casings previously supporting the integrity of the bore hole were then removed. Finally, the flow and return pipe connections were made between the drill chamber and plant room with continuous pipe lengths and all manifold connections made.
Evans concluded by saying "not only does the GRD method provide an intelligent and assured drilling process, the heat well owner should he wish to increase his heat well size at any time, the drill rig can be re-connected and additional boreholes added". (New property extensions etc).
This GRD heat well has now been in use for nine months; Charles Sterling said the combination of GRD and his Ground Source Heat Pump has been exceptionally efficient, particularly through this past extremely cold winter and he looks forward to this effortless intellectual Geothermal harvesting serving his family for year ahead.
TT UK LTD.
10 Windsor Road
Bedford MK 42 9SU
PH.: +44 (0)1234.342.566
FAX: +44 (0)1234.352.184
More News and Articles
Mar 17, 2023
Trenchless manufacturer celebrates installation of 100,000th liner
SAERTEX multiCom®’s trenchless pipe relining product, SAERTEX-LINER, has been installed for the 100,000th time.
Mar 13, 2023
Spring collaborates with Microsoft and Impact X on water innovation
The water sector’s innovation centre of excellence – Spring - is collaborating with Microsoft and Impact X on a new initiative to make tools and funding available for start-ups to accelerate their companies.
Mar 10, 2023
State of Global Water Resources report informs on rivers, land water storage and glaciers
WMO reports on freshwater availability in a changing climate
Mar 08, 2023
Australia: Centenarian sewer gets after-dark upgrade
Over 100 years since its inception, Brisbane’s S1 Main Sewer has undergone a seven-year upgrade.
Mar 06, 2023
UKWIR gives access to hundreds of water sector research reports
UK Water Industry Research (UKWIR) is providing free access to over 1,000 of its water sector research reports aimed at helping to improve water and wastewater services for customers, and protecting the environment.
Mar 03, 2023
Sector must challenge public misconceptions through engagement
The water sector must tackle “unfair criticisms” by sharing more about the great work it delivers, Yorkshire Water’s chief executive, Nicola Shaw, told attendees at British Water’s Better Together reception in Hull.
Mar 01, 2023
World-first project to ‘self heal’ cracked concrete using sludge could save $1.4 billion repair bill to Australia’s sewer pipes
Water treatment sludge could be used to prevent 117,000 kilometres of sewer pipes in Australia from cracking in future, without any intervention by humans, helping to save $1.4 billion in annual maintenance costs.
Feb 27, 2023
Delaware Water Treatment Plant Opts for Penetron to Protect New Concrete Structures
The final 2022 commissioning of the Doe Run Road Water Treatment Plant enables the city of Newark, Delaware (USA), to increase the quantity and quality of the city's drinking water to better meet growing demand – and EPA guidelines. PENETRON …
Feb 24, 2023
Aussie Trenchless: the future of pipe rehabilitation solutions
Aussie Trenchless has been passionate about progressing future infrastructure opportunities and accomplishing superior outcomes since it was founded in 2014.
Feb 22, 2023
IWA-Grundfos UN Water Conference youth delegates announced
The International Water Association and Grundfos are proud to announce that 14 bright and promising international young water professionals (YWPs) have been selected to be part of a delegation to the upcoming UN 2023 Water Conference, on 22-24 March 2023 …
Feb 20, 2023
Smart Lock makes short work: Hong Kong sewer drain repair
When the Hong Kong Drainage Services Department identified a badly damaged pipe, it was Smart Lock’s sleeve solution that empowered contractors to successfully rehabilitate the damaged section.
Feb 17, 2023
iMPREG celebrates UV Liner installation success in the UK
iMPREG has helped complete the task of installing an ultraviolet liner in the United Kingdom.
TT UK Ltd.
42 9SU Bedford MK