Hydropower plant Lago di Tomé – high pressure pipeline DN 400 for environmentally friendly electricity production
Oct 24, 2018
Installation of a DN 400 high pressure pipeline in Switzerland.
The Alpine lake known as the Lago di Tomé lies in the municipality of Lavizzara in the Vallemaggia district of the Swiss Canton of Ticino (Figure 1). The Tomé mountain stream flows from Lake Tomé into the valley of the same name and from there into the River Maggia, on the left bank just before the village of Broglio. The section between the Alpine lake, at the upper end of the valley at a height of 1,692 m above sea level, and the point where it joins the Maggia close to the village of Broglio, approximately 680 m above sea level, and hence with a geodetic head of more than 1,000 m, is of extreme interest in terms of using the water power for the production of electrical power.
The client for the construction and operation of the hydropower plant at Broglio is the newly founded joint stock company CEL Lavizzara SA.
2 The project for a small hydropower plant
2.1 General design
The new Lago di Tomé hydropower plant consists of the following components:
- Water catchment and de-sanding basin,
- High-pressure underground pipeline,
- Power plant building,
- Tail race channel for returning the water.
2.2 Water catchment
The inlet structure has been built about 120 m beneath the outflow of the Lago di Tomé lake into the mountain stream and embedded in the stony topography of the river course. Clad in natural Ticino stone slabs, the inlet building blends into the environment. The water flows through a rectangular opening beneath the level of the water into the inlet structure, meaning that no flotsam can get into the de-sanding basin (Figures 2 and 3).
2.3 New DN 400 high pressure pipeline
When selecting the appropriate material for the pressure pipeline, the clinching factors were on the one hand the tough installation conditions in the mountains and on the other hand the very high pressures of up to 100 bars with the almost exactly 1,000 m height difference. What was needed was a flexible piping system which nevertheless had to offer outstanding mechanical and static strength characteristics.
The deflectible HYDROTIGHT push-in joint makes assembly in steep terrain rapid and safe (Figure 5).
The vonRoll ECOFIT type fittings required have an epoxy coating to EN 14901  with the enhanced requirements in accordance with RAL – GZ 662 . The relatively low weight of vonRoll ECOPUR full-protection pipes was very helpful for the company constructing the pipeline in a steep and inaccessible environment because the pipes had to be transported by helicopter in order to be installed in the place of use (Figure 6).
Over the entire 3,200 m length of the pipeline route, with a height difference of just about 1,000 m, there were various and challenging installation situations to be mastered in mountainous terrain with stony, rocky ground. In order to preserve the natural appearance of the environment as far as possible, the pressure pipeline was installed underground along almost its entire length, with one exception: the pipeline crosses a stream aboveground via a pipe bridge. The almost natural reconstruction of the route was done with excavation material and natural rocks and boulders (Figures 7 and 8).
Depending on the elevation, the new pressure pipeline was designed for pressure ratings from PFA 10 bars to PFA 80 bars with ECOPUR pipes in various wall thickness classes from K 7 to K 15 with restrained push-in joints of the HYDROTIGHT type. In the upper area to PFA 16 bars, friction locking push-in joints push-in joints were sufficient to absorb the forces while also offering a large degree of flexibility with shortened pipes in the trench.
With the steepness of the terrain and because of the high operating pressures, reinforced concrete thrust blocks were positioned at points of directional change to take up the forces occurring.
Instead of using shortened pipes processed on site, the manufacturer – vonRoll hydro (suisse) ag – supplied short pipes in precisely defined lengths with welding beads applied in the factory, which are fully protected with polyurethane. This made the expensive application of welding beads and subsequent repair of the external protection at the installation site unnecessary.
In the high pressure area, as from PFA 63 bars, standard push-in fittings in wall thickness class K 12 were no longer sufficient for absorbing the forces occurring. For this application, vonRoll hydro (suisse) ag produced special fittings in wall thickness classes K 14 and K 15.
At regular intervals, inspection openings were also arranged along the pressure pipeline. These are designed as DN 400/400 double socket tees with flanged branches, also in a special design up to K 15 and with flanges for the pressure ratings necessary in each case up to PN 63 (Figure 10).
The lowest and steepest area of the pressure pipeline with the highest pressures – from 80 bars as far as the turbine house where it is almost 100 bars – was laid with welded steel pipes. For the transition area from ductile cast iron to steel, with PFA = 80 bars, once again a special fitting – flanged socket (E), with PN 100 bar flanges – was used (Figure 11).
Parallel to the pressure pipeline, and in the same trench, empty pipes were also laid for the supply cable to the equipment at the water catchment area and also for the control cable for communication between inlet and power plant (Figure 12).
2.4 Power plant building and return channel
The location of the power plant building just before the point where the Tomé mountain stream flows into the Maggia is an optimum compromise between various influencing parameters. Among other things these include the geodetic height of fall and optimum access to the equipment during the construction work and for subsequent operation and maintenance with the least possible impact on the environment.
3 Some facts about the Lago di Tomé hydropower plant
- Water catchment area 3 km2
- Height of the Lago di Tomé Alpine lake 1,692 m above sea level,
- Water catchment capacity level 1,686 m above sea level,
- Power plant building, turbine shaft 704.55 m above sea level,
- Net head height 945 m,
- Average water volume supplied 3.10 million m3/year,
- Nominal size of pressure pipeline DN 400, effective length 3,110 m
- System output of power plant 2.05 MW,
Net energy production 6.5 million kWh/year.
More News and Articles
Mar 01, 2024
Researchers in the UK and Germany have developed a new approach for detecting pollution from ‘forever chemicals’ in water through luminescence.
Feb 28, 2024
This study presents BioElectrochemical Treatment Technology (BETT) as a new wastewater management solution toward the Net-Zero future. The results reported herein were collected from a BETT pilot system installed at a large brewery in Los Angeles, CA, United States processing …
Feb 26, 2024
Following the successful pilot of its digital asset management technology with Anglian Water, Norwegian digital analytics company InfoTiles is embarking on an expanded proof of concept programme.
Feb 23, 2024
NLN Farms, located near the coastal town of Chocowinity, North Carolina, needed to transfer water from four aquaculture ponds to a nearby reservoir. The farm selected Xylem's Godwin CD100 dewatering pump for the job, with Field Smart Technology, which enables …
Feb 21, 2024
Following the devastating flooding from Cyclone Gabrielle in 2023, Watercare is acknowledging the ongoing recovery efforts one year on.
Feb 19, 2024
Our panel of international experts examines how utilities can embrace a global outlook when it comes to security.
Feb 16, 2024
The Silver Creek Water Corporation in southern Indiana manages millions of gallons of water, over hilly terrain, for 20,000 people. Over several decades, the utility has deployed technology from Xylem’s Sensus brand to remotely manage meters, prevent water loss and …
Feb 14, 2024
As the underground grows more crowded, the industry is under pressure to deliver highly accurate installations through a web of existing infrastructure.
Feb 12, 2024
In a new study, scientists at Heriot-Watt University have discovered a sustainable method to produce green hydrogen, a type of renewable fuel, using wastewater from the distilling industry. This new approach not only addresses the global challenge of water scarcity …
Feb 09, 2024
The UK water sector should give more focus to the themes of delivering resilient infrastructure systems and protecting and enhancing natural systems, according to a survey about the UK 2050 Water Innovation Strategy.
Feb 07, 2024
Drinking water scarcity is a global issue, including in Sweden, where it’s also used for crop irrigation and various industrial operations. This practice is neither sustainable nor efficient. Hence, MDU has launched an innovative research project aimed at developing efficient …
Feb 05, 2024
Industrial companies and commercial building owners wanting to reduce waste to improve cost efficiency and save water, must become smarter in their operations, writes Paul Hartley, chief commercial officer, Ovarro