Testing of Plastics Piping Systems for a Lifetime of Confidence for Domestic Applications
Jul 11, 2019
The service life of plastics is generally determined by a combination of three factors; temperature, stress (pressure) and aggressive chemicals. Members of the BPF Pipes Group have piping products which undertake extensive testing at the extreme limits of these factors to ensure that they will give excellent performance in water systems.
In the UK, the service conditions for standard domestic applications can be found in BS 7291 “Thermoplastics pipe and fitting systems for hot and cold water for domestic purposes and heating installations in buildings.” These conditions are called ‘Class S’ and are as follows (Table 1 taken from BS 7291-1: 2010):
Nominal system flow temperature
Maximum system service temperature
System malfunction temperature
System maximum working pressure A)
|Indirect cold water systems||20||20||-||3½|
|Direct mains-fed cold water systems||20||20||-||12½|
|Subsurface heating systems||60||83||100||3½|
|Vented hot water supply systems||65||83||100||3½|
|Unvented hot water supply systems including Instantaneous heaters and/or incorporating storage||65||95||100||6|
|Vented central heating systems and indirect hot water primary circuits||82||95||100||3½|
|Sealed central heating systems and indirect hot water primary circuits||82||105||114||3|
Continuously operated re-circulating systems are excluded from these applications
A) Where a nominal working pressure does not comprise an integer value, the mantissa is
expressed in a fractional format. This is done to reduce the possibility of misinterpretation or
obscurity that could cause a system to be subjected to an excessive pressure.
B) 1 bar = 105N/mm2 = 105Pa
This standard (in common with the European Standards for plastics piping systems for hot and cold water installations) includes many tests which prove suitability for these applications. The tests are designed to replicate the conditions experienced by the pipe system in use at the limits of performance. These include:
- Confirmation of dimensions – the first and most important guarantee of the performance of a plastic pipe is sufficient wall thickness to resist pressure at temperature. The dimensions of outside diameter and wall thickness are specified in BS 7291 and are measured on a routine basis by pipe manufacturers.
- Long-term hydrostatic strength of pipes – it is essential to confirm the performance of the pipe over its whole design life. Holding samples of pipe at raised pressures at various temperatures for long periods of time generates data on times to failure. Pipes at higher pressures will burst sooner than those at lower pressures. Statistical analysis of the times to failure allows a robust prediction of the maximum pressure resistance of the pipe at over 50 years or beyond.
- Hydrostatic pressure resistance of assembled pipes and fittings – the strength of the joint between a pipe and fitting is critical to the lifetime success of a system. Pressurising samples of pipes and fittings together for 1,000 hours at pressures well above the Class S rating will verify this joint strength.
- Resistance to thermal cycling of assembled pipes and fittings – the temperature fluctuations and rapid thermal expansion and contraction encountered by a domestic hot water system or central heating system can induce stress in the pipework. This has the potential to damage or age the plastics being used. Subjecting pipe samples to thermal cycle testing involves creating a closed loop system which is repeatedly cycled with cold and hot water over three consecutive stages for approximately 7½ months. The test verifies the resistance of the system to this fluctuating stress.
- Resistance to cyclic pressure shock – pressure shocks can be experienced in water systems due to the rapid closing of valves or shutting down of pumps. Testing samples of pipe at 93°C and subjecting them to a 9-bar pressure shock every two seconds (30 cycles per minute), repeated 10,000 times, will rigorously confirm the resistance of pipes to these pressure shock conditions.
- Oxygen permeability (barrier pipe) – like metals, plastics can suffer oxidation in the presence of high levels of oxygen. Plastic pipes can be tailored to provide a barrier layer to oxygen permeability. This test confirms that the barrier is effective. The level of oxygen in a closed loop recirculating system is measured at very sensitive levels to ensure it is sufficiently low to prevent oxidation of the pipe or other system components (e.g. iron radiators).
Other short-term tests are designed to give manufacturers confidence that their piping system continues to meet the requirements on a day-to-day basis. These are basic pressure tests (at raised temperatures) over a short timeframe.
Factors in installation which can affect the lifetime of a plastics piping system
All members of the BPF Pipes Group provide extensive technical assistance on the correct installation of their systems. This information will help installers and end users maintain a correctly functioning system that will give many years of satisfactory service.
Further assistance can also be found in Building Regulations and installation standards BS EN 806 “Specification for installations inside buildings conveying water for human consumption” and BS 8558 “Guide to the design, installation, testing and maintenance of services supplying water for domestic use within buildings and their curtilages – complementary guidance to BS EN 806.”
In summary, the main advice points from manufacturers are:
- Use the piping system in applications for which it is designed
- Use connectors (and pipe inserts) compatible with the pipe
- Consult pipe sizing guides to guarantee sufficient flow
- Do not exceed the specified temperatures and pressures for the application (“Class S” BS 7291-1)
- Design the system to expand and contract freely during heating and cooling cycles
- Design the system to accommodate hot water expansion
- Do not put mechanical strain on a piping system
- Carefully follow manufacturer’s guidance when connecting to a boiler
- Protect from direct sunlight
- Do not bury pipe and fittings directly in concrete (except for underfloor heating pipe) INSTALLATION
- Protect pipework during installation from damage such as scratching, chemical attack by unsuitable substances (e.g. solder flux) or heat (e.g. blow torches)
- Do not use components that are obviously damaged
- Protect the pipework during service from freezing, direct mechanical abuse or attack by rodents
- Comply with electrical continuity requirements
- Do not bend pipework excessively, twist joints or apply side load
- Correctly support the pipe (consult manufacturer instructions on clipping)
Testing and Commissioning
- Ensure unvented hot water cylinders are functioning correctly
- Always pressure test systems before commissioning
- Always disinfect hot and cold water domestic systems before commissioning. When these sensible precautions are considered, plastics piping systems provide excellent performance in water systems over a long lifetime.
More News and Articles
Aug 21, 2019
100 Years Lifetime of Polyethylene Pressure Pipe Systems Buried in the Ground for Water and Natural Gas Supply
TEPPFA and PE100+ Association have identified the need for explaining the difference between the design point at 20 degree/50 years and the expected life-time of PE80 and PE100 pressure pipe systems. Research, extrapolation studies and reports on dig-up pipes in ...
Aug 20, 2019
ams , a leading worldwide supplier of high-performance sensor solutions, Qingdao iESLab Electronic Co., Ltd., a pre-eminent end-to-end supplier of smart municipal works, and innovative water utility company Jiangxi Water Group Co., Ltd., announce plans to extend their China Water ...
Aug 19, 2019
MyTana, a manufacturer and distributor of equipment for the plumbing and drain cleaning markets, has released DrainSteer. This patent-pending product combines the functionality of a high-pressure jetter and push camera to create the first steerable, jetting drain camera in the ...
Aug 19, 2019
Valuable insights into how the water sector can manage data more effectively will be given at an upcoming British Water event this autumn. "Data: Now & Beyond" will see speakers from key stakeholders, including water companies and the supply chain, ...
Aug 16, 2019
Wastewater treatment specialist WPL has made a rapid transition to the new health and safety standard set by the International Organization for Standardization (ISO). ISO 45001 Occupational Health & Safety standard was introduced in April 2018 and organisations are advised ...
Aug 15, 2019
The Construction Site Determines the Installation Technology: Light, Steam, Hot Water or Ambient Temperature.
Which curing method should ideally be used in the context of rehabilitation projects in building and site drainage? The market for the rehabilitation of building and property drainage is currently developing dynamically. The complexity of construction sites in particular places ...
Aug 14, 2019
The first European EN standard for oriented unplasticised poly(vinyl chloride) (PVC-O) pipes came out in April 2019, after an extensive four-year development process, initiated by TEPPFA. EN 17176 PVC-O piping systems for water supply and for buried and above-ground drainage, ...
Aug 13, 2019
Suqia Extends Deadline to Apply for 2nd Mohammed bin Rashid Al Maktoum Global Water Award to 1 September 2019
The UAE Water Aid Foundation (Suqia) extended the deadline to enter the second Mohammed bin Rashid Al Maktoum Global Water Award to 1 September 2019. Applicants participating in the award will compete to win prizes totalling USD 1 million. HH ...
Aug 12, 2019
After years of collaboration between the City of Fishers, City of Noblesville, Hamilton County and Indiana Department of Transportation (INDOT) to address the traffic congestion and public safety challenges along the State Road (SR) 37 corridor, plans are underway to ...
Aug 09, 2019
Silicon Valley Clean Water Selects Name for the Tunneling Machine to Further Their $495 million Infrastructure Program
Silicon Valley Clean Water (SVCW) announced the selection of a name for their large tunneling machine that will support the agency’s $495 million infrastructure program. The program includes rehabilitating 3.3 miles of the agency’s raw wastewater conveyance piping system, involving ...
Aug 08, 2019
The city of Columbia, S.C., and Woolpert were honored by the South Carolina American Public Works Association with its 2019 SC APWA Project of the Year Award in the category of Structures/Historical Restoration for their Martin Luther King Jr. Park ...
Aug 08, 2019
On 1 June 2019, Maria Luisa Pérez Vergara (34) has been appointed Managing Director of MC-Bauchemie Belgium N.V. In this function, she is responsible for the Belgian business of MC-Bauchemie together with Benoit Verbiest (59).